Condition monitoring remains an important technology for equipment life cycle management. Historically, online condition monitoring systems are installed only on the most critical assets within a power plant, process plant, or manufacturing facility. Less critical equipment, while vital to operation of the plant, are only monitored or tested periodically using manual route based technologies. This historical practice leaves equipment specialists with a small amount of time for analysis of collected sensory data (vibration, temperature, oil, power, etc.) as they spend the vast majority of working hours collecting equipment sensory data. Fortunately, data acquisition technology has evolved, making it possible to transform standard and advanced machinery measurements from manual collections to online collections, increasing time for specialists to analyze, and yielding opportunities for automated diagnostics and prognostics. By taking advantage of automation, the ability of equipment owners and operators to lower life cycle costs and increase reliability of plant equipment is greatly improved.
The transition from manual route based measurements to a fleetwide surveillance program touches many elements from sensors to networked data acquisition nodes to servers to historians and predictive technologies. Within power generation plants, installation costs, information technology strategies, and long term vision come together to create higher machine reliability at lower operational cost and new automation in performance monitoring, diagnostics, and advisory generation. With automation, comes increased sensory data from pumps and turbines that require new tools for data management, data mining, and data transformation into actionable information. A case study reviews the open and extensible data architecture of a fleetwide monitoring system deployed, the ongoing efforts, and current benefits delivered to the power generation industry participants.
How to Cite
signal processing, vibration monitoring, Data Acquisition, Predictive Health Monitoring, pump, Data Driven
Cook, B. (2013). Duke Energy SmartM&D project, National Instruments Week 2013, August 2013.
Hussey, A. (2010), Understanding the potential of fleetwide monitoring, Energy-Tech Magazine, Woodward Communications, http://www.energy-tech.com/article.cfm?id=28887
International Standards Organization (ISO) (2003), Condition Monitoring and Diagnostics of Machines – General Guidelines, First Edition, reference number ISO 17359:2003(E), Switzerland (2003).
Lawson, K. (2010) Luminant’s condition monitoring program achieves notable successes, Reliability Web.com, online article, http://reliabilityweb.com/index.php/articles/luminants_condition_monitoring_program_achieves_notable_successes/
Monnin, M., Voisin, A., Leger, J., Iung, B. (2011), Fleetwide health management architecture, Proceedings of the annual conference of the prognostics and health management society, September 2011
Shankar, R. (2006), Fleetwide Monitoring for Equipment Condition Assessment, Electrical Power Research Institute (EPRI), reference number 1010266, March 2006
US Energy Information Administration (EIA) (2011), Electric Generator Report, Form EIA 860 and form 860M, Electric Power Monthly, March 2011.
The Prognostic and Health Management Society advocates open-access to scientific data and uses a Creative Commons license for publishing and distributing any papers. A Creative Commons license does not relinquish the author’s copyright; rather it allows them to share some of their rights with any member of the public under certain conditions whilst enjoying full legal protection. By submitting an article to the International Conference of the Prognostics and Health Management Society, the authors agree to be bound by the associated terms and conditions including the following:
As the author, you retain the copyright to your Work. By submitting your Work, you are granting anybody the right to copy, distribute and transmit your Work and to adapt your Work with proper attribution under the terms of the Creative Commons Attribution 3.0 United States license. You assign rights to the Prognostics and Health Management Society to publish and disseminate your Work through electronic and print media if it is accepted for publication. A license note citing the Creative Commons Attribution 3.0 United States License as shown below needs to be placed in the footnote on the first page of the article.
First Author et al. This is an open-access article distributed under the terms of the Creative Commons Attribution 3.0 United States License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original author and source are credited.